Squirrel cage motors configured for heavy duty in pumping station
After the failure of two squirrel cage motors in a water pumping station in Lebanon, the Tajj group – official supplier of the Lebanese Water and Energy Ministry – was looking to source replacements from a German motor manufacturer. The original motors of Italian manufacture had failed after only two years of operation, because they were unable to withstand the loads and high temperatures in the pumping station. An internet search proved successful: Berlin-based Menzel Elektromotoren GmbH could speedily replace both defective squirrel cage motors by engineering and constructing technically improved versions.
Menzel addressed the challenging operating conditions, for instance fitting the replacement motors with an IC06 forced ventilation. Though a larger size (V1) was chosen the original flange diameter and vertical design were maintained. With these modifications, the two new four pole squirrel cage motors featuring 800 kW rated power, 5500 V rated voltage and a speed of 1485 min-1 are optimally equipped to withstand overload and overheating. Menzel engineers installed and commissioned the motors which are now successfully in operation on two water pumps.